MST-1116 graphic display is a new flammable gas alarm display device launched by Minstone. It is used for the management and control of gas leak alarms and the graphic display of equipment. It forms a full-featured graphical gas leak alarm system with the combustible gas alarm controller and combustible gas detector of Maientong Company.
The main unit of the graphic display is an industrial control computer. The interface board inserted in the industrial control computer is connected to the controller. The industrial control computer reads the controller information and processes it in a graphic display. The host computer can also use LAN, RS-232 / RS-422, etc. Networking, receiving, sending, and displaying the abnormal information of the equipment and the host information, so as to realize the combined operation of the driving graphics, data, and business of the gas leak alarm.
| Use environment || Temperature: 0 ℃ ～ + 40 ℃ Relative temperature ≤95%, non-condensing |
| voltage || AC220V 50Hz 0.5A |
| Host configuration || Memory: 512M or more CPU: P41.8G or more |
| operating system || WinXp (IE6.0 or above) |
| screen size || 21.5 inches |
| Resolution || 1920 × 1080 / 60Hz |
| touch screen || Capacitive + point touch |
| Network card || Gigabit LAN |
The upper computer is a non-explosion-proof structure. It should be fixedly installed in a safe place. The true installation location should be selected for easy observation and maintenance. The surroundings should not affect the strong electromagnetic fields (motors, transformers, power cables, etc.) of the equipment. working principle
This machine uses 19 o'clock screen and large screen integrated industrial control computer (Tuchuan, RS-232, RS-485 signal communication), and the corresponding controllers of the received controller are transferred to the CPU for analysis and processing, and make corresponding Text display, sound and light signal and sound output signal. Pay attention
When the distance between the host computer and the controller is less than 15 meters, the RS-232 bus can be directly connected (if any). When the distance between the host computer and the controller is greater than 15 meters, it must be connected with an RS232-RS485 converter.
Please pay attention to our company's WeChat: "szmsn-", Chinese "Shenzhen Maistone Technology", or scan the QR code below: